CITB has developed this standard in discussion with industry
Minimum 1 day of 6 learning hours per day
The purpose of this standard is to provide the candidate with knowledge of ventilation systems.
The scope of this standard covers:
- chimneys and flues for: coal, oil, biomass, wood, and gas
- how to technically interpret regulatory directives
- how to technically interpret manufacturer’s installation instructions
- how to calculate size of combustion air supply
- test evaluation methods and processes
- how to avoid oxygen starvation
- ventilation for open fires
- direct to air appliances (potential faults and legal requirements)
- main legislation, codes of practice, building standards, and BS/EN standards, relating to the design and installation of flues, including fire, safety and environment.
Training delivered against this standard would be relevant to the following occupational groups:
- operative and craft
- management and leadership.
There are no candidate pre-requisites as part of this standard. However, it would be beneficial if candidates had experience in the relative industry.
As a minimum, course instructors must be able to demonstrate that, in relation to this standard, they have:
- a train the trainer or instructional techniques course certificate
- successfully completed training to this standard
- at least 2 years relevant industrial experience
- a verifiable CV.
The following methods may be used in the delivery of this standard:
All materials and equipment must be of a suitable quality and quantity for candidates to achieve learning outcomes and must comply with relevant legislation.
The class size and candidate/instructor ratio must allow training to be delivered in a safe manner and enable candidates to achieve the learning outcomes.
This standard is considered to contain 51 per cent or more theoretical learning.
For the successful completion of training, candidates must complete an end of course practical assessment or knowledge test that measures the learning outcomes and has a pass or fail criteria.
Quality assurance against this standard will require initial approval of the training organisation and their content mapped to the standard.
CITB will also conduct an approval intervention, either desk-based or centre visit, to ensure the training organisation can meet the requirements of the Training Standard.
Approved training organisations (ATOs) will be required to present information on records of training and assessment upon request to CITB for desk-based analysis. They will also be visited annually by the CITB quality assurance team.
There are no mandatory renewal or recommended refreshment requirements for this standard.
Either on request or in 3 years from approval date.
|The candidate will be able to ||Additional guidance to support learning outcome
Describe how to technically interpret regulatory directives
Extracts of regulations and standards
Describe how to technically interpret manufacturer’s installation instructions
Samples of manufacturer instructions with corresponding photos of kit and installation
Describe how to calculate size of combustion air supply
Provide scenarios. Use calculator, phone app, and/or spreadsheet
Describe test evaluation methods and processes
Photos of equipment and videos of use
Describe how to avoid oxygen starvation
Describe ventilation for open fires
Describe direct to air appliances (potential faults and legal requirements)
Photos/illustrations of faults, with corresponding extracts of applicable regulations
Additional information about this standard
The construction and installation of chimneys and flues is covered by UK building regulations in conjunction with relevant European and British standards.
Additional information is also available on the NBS website.
The Planning Portal website holds further information on:
Health & Safety Executive (HSE)
There is a lot of HSE information relating to chimneys and ventilation systems. Some examples are:
Working at height
The BSI website holds the following British/European standrds and codes of practice:
- BS 1251: 1987 Specification for open fireplace components.
- BS 5440-1: 2008 & 2:2009. Flueing and ventilation for gas appliances (70 kW net).
- BS 6762-2:1991. Code of practice for solid fuel fired heating in park homes and caravans.
- BS 6880. Parts 1,2&3 1988. Code of practice for low temp hot water heating systems (45kW+).
- BS 7977-1&2: 2009 Spec’n domestic gas appliances. Radiant. Combi/gas fire/back boiler (Pt2).
- BS EN 483: 2000 Gas-fired central heating boilers. Type C, max 70kW.
- BS EN 509: 2000 Decorative fuel-effect gas appliances.
- BS EN 13384-1 & 2: 2015 Chimney thermal/fluid dynamic calcs for one/more heating appliances
- BS EN 15287+A1: 2010. Design, install & commission chimneys. Non & roomsealed appliances
- BS EN 50291-1: 2010. Domestic electrical apparatus for detecting carbon monoxide.
- Chimneys and flues
- BS 715: 2005 Specification for metal flue boxes for gas-fired appliances (max 20kW).
- BS 4207:1989. Code of practice for monolithic linings for steel chimneys and flues.
- BS 5854:1980. Code of practice for flues and flue structures in buildings.
- BS 6999:1989. Specification for vitreous-enamelled low carbon steel flue pipes
- BS 5871: Parts 1,2,3: 2005 & Part 4: 2007. Specification for installation of appliances
- BS EN 1443: 2003. General requirements for chimneys
- BS EN 1856 – 1&2: 2009. Metal chimneys, products (Pt1) and liners/flues (Pt2)
- BS EN 1857: 2010 Concrete flue liners.
- BS EN 1858: 2008 +A1:2011 Chimneys, components, and concrete flue blocks.
- BS EN 1993-3-1: 2006. Eurocode 3. Design of steel structures. Towers, masts and chimneys
- BS EN 12446: 2011. Concrete outer wall elements.
- BS EN 13084-1,2,4,5,6,7 2007. Free-standing chimneys. General, concrete, brick, and steel
- BS EN 14241-1: 2013. Chimney elastomeric seals and sealants.
- BS EN 14471: 2013+A1:2015. Chimney systems with plastic flue liners.
- BS EN 16497-1&2: 2015. Concrete chimneys. Non-balanced (Pt1) and balanced (Pt2) flues.
- Requirements and testing
- BS EN 1457-1&2: 2012. Clay/ceramic flue liners, dry (Pt1) and wet (Pt2).
- BS EN 1806: 2006 Clay/ceramic flue blocks for single wall chimneys.
- BS EN 1859: 2009 +A1:2013 Metal chimney test methods.
- BS EN 13063-1&2:2005 & 3:2007. Clay/ceramic flue liners. Sootfire resistance.
- BS EN 13069: 2005. Clay/ceramic outer walls.
- BS EN 13216: 2004. Test methods for chimney systems.
- BS EN 13502: 2002. Clay/ceramic flue terminals.
- BS EN 14297: 2004 Freeze-thaw resistance tests for chimney products
- BS EN 14989-1&2: 2007. Metal chimneys.
- BS EN 16475-1,2,3,4,5,6&7. 2016/2017. Chimneys. Accessories. Silencers, Fans. Draught regulators, standstill opening devices, combi-secondary air devices. Access parts. Rain caps.